Honeywell FC100A1037 Air Filter 20 x 25 x 4.5
List Price: $51.51 Sale Price: $34.99
The FC100A series filter is a cardboard frame box style filter made up of a web of fibers (MERV 10). As air passes through the filter media, particulates such as dust, pollen, dander, mold, and bacteria collide with the fibers in the filter and become trapped. Meanwhile, the clean air is allowed to continue through your heating and cooling system and into your home.
Replacement Schedule The media filter must be replaced when pressure drop across the media filter reaches 0.5 in. w.c. (0.1 kPa), or at least annually. If the media air cleaner is installed downstream from an atomizing humidifier or if the installation includes both heating and cooling, more frequent replacement may be necessary. Clogged media must be replaced promptly to avoid restricting airflow and reducing efficiency of the heating/cooling system. Record the replacement date in the space provided on the replacement media filter.
Other Options Honeywell released the POPUP series media as an optional replacement for the FC100A series filters. This new media ships collapsed and a higher efficency (MERV 11) which expands into place with no tools required. The new POPUP style media is wider than the old FC100A series media and WILL NOT work on non-Honeywell air cleaners. If you are interested in the POPUP media click on the related product shown below for additional information.
The filter media is not cleanable and must be replaced a minimum of twice a year, once in the heating season and again in the cooling season. If your home only has heating, the filter must be replaced annually. Please note, if you have shedding pets, or live in a dusty environment, you will need to replace the filter media more often.
- 19 7/8 (inches)
- 24 7/8 (inches)
- 4 3/8 (inch)
- MERV Rating:
- Indicated on Product
Filter by Don Hollister (Scottsdale Az US)
Exact filter I needed by Donna Whitefield (Camas WA US)
These are hard to find and I am very happy with the price and delivery
Air filter for home unit by Ellen S Wakefield (Watauga TX UG)
Like the fact that the filter I need for my Air unit, is available for me to order on line since I cannot get in the retial stores. My unit requres a large filter 20x25x5. When I order you get it right to me. So far I have been very pleased with the products. Wish it cost less.
Home Filter by P. Stuart (Conroe TX US)
Superb Filter, works like a charm.
ac filters by eduardo (sica te US)
The product is great. I have to say that one of the two filters got dented during transportation, so I hope it will work properly. Eduardo Sica
Replacement parts by Richard F. Pecovsky (Virginia Beach Va US)
Admin Assistant by DAVID BUSINESS MACHINES (GREAT FALLS MT )
ORDERING THE PRODUCT WAS VERY EASY AND WE RECEIVED THE FILTERS BEFORE THE SPECIFIED DATE.
Rating by William F. Butterfield (Spring TX US)
It confused me a bit because it came folded.
New Furnace filter by Carolyn Trotter (Camarillo CA US)
The filter was easy to assemble and install. It fits my new Lennox furnace just fine. I will order this product again. Thanks for asking.
FC100A1037 Filter Media by Franklin Bates (Allen Te US)
When UPS brought your package to our door, I thought there had been a mistake. That small box could not possibly hold three (3) Honeywell filters like the ones I have been buying for more than six (6) years. I was amazed to find that the box did, indeed, contain three (3) Honeywell filters that easily "popped out" to full size! Very clever design - it makes it easier for me to handle and transport the filters to the attic for installation in three (3) AC units. Thanks!
New replacement filter by ( )
Overall, the reordering of my replacement filter was very easy and it was a very quick process.